The rule is simple as Four-Terminal sensing (4T Sensing): to separate current-carrying path and voltage sensing probing.
For Sentry battery monitor installation, keep in mind that the sensing O-rings have to be in close contact with connection bar without any washer in between. (O-ring shall not be placed between connection bar and battery post. That will compromise battery bank connectivity).
Stainless steel bolt and washer have high resistance. If installed as “RED”, battery#1, #6/#7 and #12 will have wrong measurement, which will lead to wrong battery health “SOH” estimation and trigger alarms.
Enjoy your fine work!