This Method of Procedure (MOP) has been created for the installation of a Battery Management System (BMS) in power plants and substations, utilizing the BatteryDAQ Sentry-6002NEMA (125/250VDC) and Sentry-2402NEMA (-48VDC) devices.
The installation should be performed by qualified service personnel who are knowledgeable about batteries and the necessary precautions that should be taken.
- Please take BatteryDAQ’s in-class, on-site or remote training.
- Please prepare and follow “Safe Work Plan – Electrical & Arc Flash Hazard Mitigation” guideline for specific site and battery.
[Safe Work Plan shall be available with this MOP before installation starts.]
- Other client site requirements
Part#1 – Mounting and Wiring
Sentry-6002 measurement unit connects to battery posts, 3 temperature probes and current transducer via 12 multi-conductor (12C) cables. Please read this panel carefully to understand the name and purpose for each pin.
Choose the best and secure location to mount the NEMA box, so the cable length can be evenly spaced.show less
Part#2 – Setting and Verification
Part#3 – SCADA and Dashboard
Part#4 – NERC Report
Part#5 – Load Test
Part#6 – Data-driven Battery Services
Download Word and Pdf Files
|Document Name||Word Version||pdf Version|
|MOP Part#1 – Mounting and Wiring||Part#1 (.docx)||Part#1 (.pdf)|
|MOP Part#2 – Setting and Verification||Part#2 (.docx)||Part#2 (.pdf)|
|MOP Part#3 – SCADA and Dashboard||Part#3 (.docx)||Part#3 (.pdf)|
|MOP Part#4 – NERC Report||Part#4 (.docx)||Part#4 (.pdf)|
|MOP Part#5 – Load Test||Part#5 load-test|
|MOP Part#6 – Data-driven Battery Services||Part#6 (.docx)||Part#6 (.pdf)|
|Sentry-6002NEMA Connection Schematics (High Resolution)||–||Schematics (.pdf)|